Payment & Shipping Terms:
|Type:||Current Fuse||Fuse Device:||Pop-up Soild|
|Rated Voltage:||12 Kv~24kv||Altitude:||Up To 3,000m Above Sea Level|
|Typical Products:||Protection Fuse||Warranty:||2 Years|
high voltage fuse,
drop out fuse
PRW10-12F/100Series loadbreak fuse cut out(hereinafter referred to as fuses)is used for overload and short-circuit protection and openning and closing rated load current.
The product can be used in AC50HZ,rated voltage of 10KV distrbution lines and distribution transformer.
|Rated voltage kV||Rated current A||Rated breaking capacity MVA||Opening/closing times of load current||Weight kg
Silicone rubber can be reduced 2kg
|Lower limit||Upper limit|
1. Low minimum breaking current, low power losses and low arc-voltage
2. High breaking capacity and effective short-circuit prospective current limitation
3. Fuses are the fastest overload protection devices for high short-circuit currents
4. Applying the superior insulating material,large creepage distance and suitable for different environment
This kind of fuse consists of three parts: fuse base, load arc- extinguishing device and an arc extinguishing device.
Active and static contactor is of bridge structure. While fuse is in closing position, active static contactor will be tightlypressed by compressed spring to guarantee a suitable pressure between contactors. A rotary torsion spring is equippedin the lower end of arc extinguishing tube. When a fuse-element is put in the tube the torsion spring will be screwed tightly,the fuse will be in drawing tightly condition to ensure the arc-extinguishingtube self-locked in closing position.
When overload or short-circuit occurs, fuse-element will be melted and the fuse will be quickly drawn out from the fuse tube by the torsion spring. Meanwhile, a great deal of arc-extinguishing gas is produced in the fuse tube by electric arc heat energy to extinguish electric arc quickly.
After electric arc-extinguishing, the voltage between the both ends of the fuse is regained. The fuse tube will be dropped out by its weight and a function of compressed spring with bridge contactors.
So an obvious disconnected section will be produced. Arc-extinguishing tube is designed at a step by step gas-discharging type. While breaking a low current gas produced will be released from the lower vent. While breaking a high current, the gas produced will be released from the upper cap to realize a gas release from both the top and the bottom, which meets the requirements of breaking different current in the same time.
Contact Person: admin