Payment & Shipping Terms:
|Special Conditions:||Depends On The Customer||Tap Changer:||Regulate The Output Voltage|
|Rated Frequency:||50||Altitude:||<1,000m (Above Sea Level)|
power distribution substation,
packaged transformer substation
Wind Power / PV Packaged Transformer Substation / Power distribution substation
YBT13 Series PV and Wind Power Special Substation is researched by our company in order to meet the demand of wind power and photovoltaic generation, The product has novel appearance, compact structure, reliable performance, easy maintenance, etc.
1. Enclosure Structure
a. The frame of substation: channel steel and angle steel.
b. enclosure materials: cold rolled steel plate, stainless steel plate, composite color plate or aluminum alloy plate.
c. Steel plates are used to isolate each bay, and equipped with lighting device.
d. The roof: double-decked structure to prevent the heat radiation effectively.
e. Transformer room is divided into open type and closed type .The radiator is located outdoor for the open structure While the closed type structure has a separate room where an automatic air exhausting device is provided to control the temperature in transformer room.
f. Housing doors : low temperature type sealing strip which can achieve good sealing effect under low temperature environment.
g. The paint on the surface of the substation is dealt with baking varnish in high temperature so that it can delay the degradation arising from ultraviolet ray effectively.
2. HV Unit
1. Make various combinations at consumers’ requests,which are HXGT16-40.5, XGT5-40.5 and HXGT10-40.5 switchgears.
2. HXGT16-40.5 switchgear equipped with FT16-40.5R type load switch-fuse combined switch for wind power and photovoltaic power generation.
c. XGT5-40.5 switchgear equipped with VT16-40.5 circuit breaker.
d. The switchgear has the complete function for prevention of misoperation to ensure safety of operation and maintenance.
3. Transformer Unit
a. Transformer uses S11 type oil-immersed transformer or SCB11 dry type transformer.
b. Natural ventilation is good in transformer room or the temperature in transformer room can be lowered through the exhaustion of the wind with automatic control fan.
c. Soft connection is used between terminals on LV side and busbar, which can effectively protect LV bushing of the transformer from crush and oil leakage.
4. LV Unit
a. LV switchgear uses TANW1 series smart CB and TANM1 series MCCB, or the CB produced by designated manufacturer at customers’ request.
b. Curtained scheme can be designed according to the user’s requirements.
5. Distribution Network Automation unit
a. Automatic terminal equipment is TA-D20 type from Tianan Group, its design has been optimized after taking severe environment for the operation of wind power substation into consideration.
b. The product has strong ability to adapt the ambient temperature, communication function of dual fiber optic ring network, the strong ability of anti-interference, shockproof, moisture proof and anti-thunder, as well as low power loss.
c. The product has the functions of measurement control, non-battery protection, and data processing, monitoring alarms and abnormity detection and communication.
6. Uninterruptible Power Supply special for the power
a. Substation is installed TA-UP01/TA-UP02 uninterruptible power supply special for wind power produced by Tianan Group.
b. The product has strong ability to adapt the environment, resist shock and interference, and wide range of stabilivolt.
|HV Unit||Switch Type||Combined Electrical Apparatus||Circuit Breaker|
|Rated Main Busbar Current||A||630||1250|
|1min Rated power Frequency Withstand Voltage To earth, Between Phases/to open gap||kV||95/118||95/118|
|Lightning Impulse Withstand Voltage To earth, Between Phases/to open gap||kV||185/215||185/215|
|Rated Short-time Withstand Current||kA/s||20/2||25/4|
|Rated Peak Withstand Current||kA||50||63|
|Rated Short- circuit Making Current||kA||31.5||63|
|Rated Short-circuit Breaking Current||kA||31.5||25|
|LV Unit||Rated Voltage||V||690|
|Rated Main Circuit Current||A||1600～3300|
|Rated Limit Short-circuit Breaking Capacity||kA||50|
|Rated Operating Short-circuit Breaking Capacity||kA||40|
|Rated Short-time Withstand Current||kA/1s||40|
|Transformer Unit||Rated Capacity||kVA||1600～5500|
|Resistance Voltage||%||4； 4.5|
|Tapping Range||%||±2X2.5； ±5|
|Connected Group||Y,yn0； D,yn11|
|Enclosure||Degree of Protection||HV Room||IP33|
Contact Person: admin